- Tech info of R410A
AVERAGE COP 10 at Air 26℃/ Water 26℃/ Humidity 80%
(COP means Coeffcient of Performance, it is a ratio of heating capacity to power consumption)
Half running cost principle (in 180 days swimming season)
In the first 5 days a Inverter-plus Commercial T3 pool heat pump runs at 100% capacity and heats up the pool to the set temperature. In the next 175 days it runs at AVERAGE 50% capacity by AVERAGE COP 10 to maintain the desired pool temperature. So the AVERAGE COP is double of On/Off heater.
• Super Silent
AVERAGE 10 Times Quieter
When maintaining pool temp at AVERAGE 50% capacity, it brings a quieter swimming environment with twin-rotary DC-inverter compressor and unique ventilation system.
• Long Working Life
Low speed running philosophy extends working life.
• Soft Start
When Inverter-plus Commercial T3 pool heat pump turns on,the current will start from 0A and go up slowly to rated current in 2 minutes. It will not affect the house electricity system, while the frequent start current of On/Off heat pump is 5 times of rated current, it is a burden to the electricity system.
|Inverter-plus Commercial T3|
|Advised pool volume (m3)||100~150||150~300|
|Operating air temperature (℃)||0~52|
|Performance Condition: Air 26°C, Water 26°C|
|Heating capacity (kW)||50.0||90.0|
|COP at 50% capacity||10.8||10.6|
|Performance Condition: Air 45℃,Water 32℃|
|Cooling capacity (kW)||26.0||45.0|
|Heat exchanger||Spiral titanium tube in PVC|
|Rated input power||1.71~8.56||3.30~15.5|
|Rated input current||2.47~12.36||4.76~22.4|
|Net dimension LxWxH (mm)||1000x1110x1260||2100×1090×1280|
|Net weight (kg)||212||459|
|Qty per 20’FT / 40'HQ (sets)||8/18||4/9|